||37,000 square feet of total enclosed space. 20,000 square feet of 36 inch raised floor.
||Fed from three Power and Light dual-fed 2000KVA transformers. Four 2000KW diesel generators feeding parallel redundant UPS systems, comprised of three 900KW UPS capacity N+1 configuration; Generators and UPS are N+1 redundant; Seven days of fuel will be on-site and will enable the facility to run at full capacity for one week. All power cabling below floors is installed in either conduit or sealtight flexible conduit with approved connectors to all equipment.
||Direct fiber access to multiple carriers. Copper or fiber access to carrier bandwidth using cable management trays throughout building.
||All building entrances require card key access; Data center floor and secured areas require card key and two-factor biometric authentication (finger print and iris scan) with a “man-trap” entrance. CCTV monitoring, single site entrance with security office and secure check-in; Property surrounded entirely by a seven foot high fence. Guards on site 24/7x365; Active patrols both inside and outside the facility. Cameras cover inside and exterior of building, property perimeter, all entrances, alternate workspace, and data center floor; Roof of building is monitored with CCTV and motion detectors. VESDA (Very Early Smoke Detection Apparatus) provides earliest possible warning of a potential fire event by detecting smoke particles at the incipient stage of fire. Pre-action dry pipe system requires alert from two sensors, activating pipe fill and a final stage when temperature exceeds thresholds.